9 Mistakes To Avoid In Your SWAS Specs
Create perfect fossil power plant SWAS specs every time
Sentry Equipment/Rebuild-It Services will be closed from Monday, December 26th through Friday, December 30th. We will reopen on Monday, January 2nd.
The Sentry DCCP Reboiler Degassed Cation Conductivity Panel is designed to optimize the analytical results for degassed cation conductivity. First, the panel uses an oversized heater and baffled vapor discharge chamber, which assures complete boiling and provides a steam blanket over the sample to eliminate any sample contamination that might occur due to discharge piping backflow on the exhaust vent. Second, after the sample is degassed, it is cooled with an additional sample cooler so that chemistry deviations in analyzer temperature compensation curves are reduced.
The DCCP is a complete panel that measures specific cation and degassed conductivity or any individual measurement needed. The custom analysis panels include degassed conductivity, dissolved oxygen (DO) and corrosion products sampling. The panel is designed to work with a wide variety of conductivity analyzers and provides simple and compact cycle chemistry validation.
|Max. Flow Rate (cc/min)||200|
|Max Process Pressure||100 psig (6.9 barg)|
|Process Temperature||130°F (54°C)|
|Flow Rate||100–200 cc/min|
|Input Power||110–120 Vac, 1 phase, 60 Hz or 220–240 Vac, 1 phase, 50 Hz|